The whole sewage pump is made of stainless steel to meet the occasions with corrosive medium. It has no blockage, automatic coupling equipment, motor monitoring system and water leakage maintenance function. It is widely used in sewage drainage stations in residential areas. Discharge of thin mud in municipal engineering and construction site. Water supply equipment of waterworks. Farm sewage discharge and rural farmland irrigation. Supporting exploration mines and water treatment equipment. Instead of carrying people on their shoulders, they suck river mud. Wastewater discharge of enterprises. Urban sewage treatment plant discharge system. Subway, basement, civil air defense system drainage station. Sewage discharge from hospitals, hotels and high-rise buildings. Jog the motor to see if the motor turns correctly. Start the motor. When the stainless steel blowdown pump works normally, open the outlet pressure gauge and the inlet vacuum pump. After it shows appropriate pressure, gradually open the gate valve and check the motor load together. Try to control the flow and head of the stainless steel water pump within the range indicated on the sign, so as to ensure that the stainless steel water pump works at a higher working efficiency point, so as to achieve greater energy-saving effect. During the operation of stainless steel sewage pump, the bearing temperature shall not exceed the ambient temperature of 35C, and the higher temperature shall not exceed 80C If the stainless steel sewage pump is found to have abnormal sound response, park immediately to check the reason. Check whether the stainless steel sewage pump, pipeline and joint are loose. Roll the stainless steel water pump by hand to see if the stainless steel water pump is flexible.
Does the liquid ring pump have requirements for the working fluid?